- This topic has 41 replies, 1 voice, and was last updated 14 years, 4 months ago by finn.
18th July 2008 at 10:23 #49232PrinceGuest
The battery not charging, is it a 2216 cabinet or 2116 or 2206? I mean which type of cabinet are you talking about.18th July 2008 at 12:27 #49233ahmad khatamiGuest
tks for your responce
but i want to know cable diagram
so each pin number connect to other side of cable
for example 2 to 3 and 3 to 2
and so19th July 2008 at 15:18 #49234PrinceGuest
DB-9 serial cable has the below mapping of female to male:
Thanx.19th July 2008 at 15:27 #49235PrinceGuest
Cannot provide the diagram using this forum but I can give you what each pinout does and the signal it transmits.
Pin Description signal
1 Carrier detect CD
2 * Receive data RD
3 * Transmit data TD
4 Data terminal ready DTR
5 * Signal ground SG
6 Data set ready DSR
7 Request to send RTS
8 Clear to send CTS
9 Ring indicator RI20th July 2008 at 06:26 #49236jamilGuest
Hi prince I am working in RBS 2116 I faced problem battery disconnect when they are using the microwave to make aliment without but my question now is about the cable alarm at the PFU its 8 alarm do u know every alarm what it means .
jamil23rd July 2008 at 17:09 #49237PrinceGuest
For 2116 and 2216 cabinets, if the battery is not charging or the RBS can’t run on battery when there’s no power at the site, it actually means two things:
1. There is a breaker panel on the topmost part of the BBS that controls the BFU. This panel has a numbered breakers on it starting from 1.We normally tap power from that panel and give it to the transmission equipment.Check if the 1st breaker is in the on position, if it’s not on just put it on and the battery from now onwards will charge and can sustain the site when power is off.
2. The BFU can internally have battery disconnect alarm without showing this alarm on the BFU.So when such a thing happens you just have to change the BFU.
thanks.25th July 2008 at 00:02 #49238finnGuest
BFU is not defined in RBS2216 so you might need to energize or like a jumpstart the BBS batteries. you’ll have to parrallel a fully charged battery. But be very careful. Once energized it will click or trigger on the BFU or yeah replace it if still the same.25th July 2008 at 18:01 #49239Hi princeGuest
In most of BBS cabinet for the RBS 2116 when the battery less them 22 volt the BFU will not charging the internal relay inside the BFU will not get order from the microcontroller. I had make a physical thing let it charging but if any one use it and don’t know how may be it coast to burn the BFU so sorry I can’t speak about it but for me it work 100% also I the new version from omt 35-4 it can configure the 4 psu in 2116 cabinet thanks all .
jamil el banna10th August 2008 at 03:25 #49240alirezaGuest
i have problem on cf( flash memory carid) max capacity cf ?
and if read with reader cf it is ok?12th September 2008 at 05:00 #49241finnGuest
I think its 32MB.. read with card reader, no drama.19th September 2008 at 13:19 #49242FadiGuest
how i can connect External alarms to RBS 2216 ??20th September 2008 at 06:12 #49243finnGuest
external alarm connections is very much different with older RBS. there is a different color coding, it should be provided. usually the external alarm cable from the DXU-31 is a like a SCSI connector type and the end sides where distributed to 4 RJ-45 connectors.. but we cut those RJ-45s and trace 1 by 1 which is which.
- The forum ‘Telecom Design’ is closed to new topics and replies.